If your boiler is losing pressure, there’s a good chance you’ve been told to adjust this pressure using the filling loop to “top up the boiler”. My advice would be. Don’t.
Hopefully, the installer dosed your system with inhibitor as well as fitting a scale reducer (in hard water areas) and a magnetic system filter.
Inhibitor breaks down any bad particles in the system, allowing the scale reducer to catch them. Every time you top up the boiler using the filling loop, you are diluting the inhibitor that’s in the system.
Here are some of the reasons that result in a boiler losing pressure. And of course, if you need a boiler repair specialist, get in touch.
#1 – Pressure Relief Valve is Faulty
#2 – Auto Air Vent Leaks
#3 – Leaking Radiators, Towel Rails and Radiator Valves are Leaking
#4 – Radiators Are Full of Air
#5 – Dodgy Expansion Vessel
#6 – Soldered Joints are Leaking
#7 – The Pressure Gauge is Faulty
Most boiler operate at 1.0bar-1.5bar. But they can approach 3bar if there is a problem. A pressure release valve notices this abnormal change in system pressure and releases it. If the PRV has failed, it will cause the boiler to lose pressure.
Central heating systems can collect air pockets over time (and they certainly do when they are refilled).
Bleeding the radiators is the best solution, but the auto air vent (which is normally inside the boiler casing on newer combis) can also help to combat this problem.
However, if the auto air vent is faulty, it could be losing pressure.
This is the most common cause when looking at boiler pressure loss. The smallest of leaks can cause your system to lose pressure.
Do a visual check of all radiators, radiator valves and towel rails. If there is any sign of water escaping, then this is the likely culprit. A small weep on a radiator valve is enough to cause pressure loss on your boiler.
If the connections are extremely loose, tightening them up (carefully) will usually solve the issue. If it doesn’t, the culprit will need to be repaired or replaced.
For the time it takes to drain down a system, replacement is usually the better option.
If you’ve had work done to your central heating system, it may have collected some air in the radiators and towel rails. You can release this pressure by using a bleed key.
To bleed radiators and towel rails, simply open the vent with the key slightly. You’ll start to here air hissing out. Once the air stops water will start to drop out (or spray out if you’ve open the vent too much). Close the vent off. Do this to every single radiator and towel rail in the property.
It’s worth taking a small container to collect any water and a towel to protect carpets.
Remember if you are constantly removing air, the pressure will drop each time you bleed the radiators.
Every now and then expansion vessels will need to be repressurised. If they are not, they can affect the pressure of the boiler. In some cases, the boiler losing pressure could be for this very reason.
A more likely cause though is the Schraeder valve is leaking. This is the valve on the vessel that will look the same as your car inner tube valve. A faulty valve can cause pressure loss in a boiler.
Another possibility is that the diaphragm on the vessel has degraded over time and the pressure is being lost there.
If repressurising the expansion vessel doesn’t work, or the suspect is a diaphragm or Schraeder valve, the vessel will need to be replaced to stop the boiler losing pressure.
As we’ve already mentioned, leaks are the most common cause a boiler losing pressure. If your system is particularly old, there’s a good chance soldered joints have become weak. You only need a tiny leak for a system to start losing pressure.
If you can find the leak, call a Gas Safe engineer to come and re-solder the joint to stop the leak. Use the filling loop to get the boiler pressure back to where it should be and see if there is any pressure loss.
This is unlikely, but it’s happened before. There’s a chance the pressure gauge on the front of the boiler is not reading correctly.
This is quite dangerous, especially if you are constantly topping up the pressure. It’s likely that this is the case if you top up the pressure and nothing happens (or the pressure changes very little).
If the pressure doesn’t change and it’s not the pressure gauge, that’s a sign of a leak that you’d almost certainly notice!
Struggling to understand why your boiler is losing pressure? Leave a note in the comments and we’ll get back to you.