Alot of boiler issues stem from central heating pump problems. This can include a range of faults including leaks, noisy boilers, or even radiators not working.
If you have any questions relating to heating pump problems, please leave a comment below and we’ll get back to you.
You can also get a free quote and advice from one of our engineers by filling out this boiler pump repair quote form.
How Does a Heating Pump Work?
The pump in a central heating system takes hot water from the boiler and pumps it around the pipework in your property. This feeds the radiators, taps, towel rails and showers in your property. If a central heating pump is not working, it can wreak havoc on your whole heating system.
Where is the Pump Located?
Central heating pumps are located behind the casing on the boiler.
We’re going to cover the most common heating pump problems and what can be done to fix them (or, how much they cost to fix).
Pump Problem 1: The pump is running, but it’s not pumping water around the system
Pump Problem 2: Pump is Blocked Full of Dirt
Pump Problem 3: Airlocks & Noisy Pumps
Pump Problem 4: Incorrect Installation
Pump Problem 5: Pump Speed Settings are Incorrect
Pump Problem 6: Leaking Pump
Pump Problem 7: No Power
Pump Problem 8: Pump Won’t Turn Off
If the heating pump is running, then it should be vibrating slightly. The most likely cause of this problem is that the shaft or propeller on the pump is stuck.
On some occasions (especially when the motor is extremely hot), the pump’s motor is the problem. The pump will get warm, but it shouldn’t be hot to the touch.
This is particularly common on heating systems that have been left sitting for a while.
If a component on the pump is stuck and the pump is not circulating, sometimes a gentle tap will free up any seized components.
If the seizure is happening on a regular basis, it’s a good sign the heating pump is on its way out and is likely to fail altogether.
A replacement pump is likely to cost £200-250 including installation. This is for a top brand pump such as Grundfos.
As central heating systems age, dirt and metal particles from radiators and pipework break down and begin to flow through major components such as the heating pump. This dirt and grime builds up in major components in the boiler and causes them to fail. Luckily, pump blockages are quite easy to fix, as all it requires is a little bit of cleaning.
It’s common for the boiler pump to build up with dirt and then stop working correctly. When this happens, you’ll find your heating system heats up slowly, not to full temperature, or not at all.
The first point of call would be to hot flush the heating system with chemicals. This differs to a power flush as it doesn’t increase the pressure in the system. Increasing the pressure on old systems can weaken joints and components and cause leaks.
Once the system has been flushed and the pump has been clean, a good preventative measure is to fit a magnetic system filter.
The magnetic system filter will catch a lot of the debris and help to prevent any future heating pump problems.
Always ask an engineer to check the heating pump when they come to do an annual boiler service.
Another common heating pump problem is air locks. If air builds up in the pump, the pump will stop working correctly.
Many heating pumps have a bleed screw that can be used to remove the air, and allow the pump to work again without replacing any internal parts.
If you hear noises coming from the pump that don’t seem normal, airlocks are likely to be the problem. A lot of customers complain of a constant humming noise when airlocks are the problem.
Once the pump has been located on the boiler, look out for a small bleed screw. Please bear in mind that the pump is full of water. Open the screw extremely slowly (less than a quarter of a turn will usually be enough) as there is likely to be a small amount of water leaking out of the pump once all the air is bled.
If this doesn’t fix the problem, it’s likely the pump noises have always been there. Some manufacturers supply anti vibration brackets which are easy to install.
Not all heating pump problems can be blamed on the pump. If the system has never worked correctly, there’s a small chance that the pump may have been installed incorrectly. In a worst-case scenario, the pump has been fitted the wrong way.
This is extremely uncommon, but if the pump has been fitted incorrectly, then it needs to be switched around. Remember, the system must be drained down before the pump can be removed and then turned.
After refitting the pump, the system will need to be filled using the filling loop on the boiler. And remember, all radiators and towel rails will need to be bled.
Newer pumps (such as the Grundfos 15/60) will have speed and flow settings. They are extremely easy to adjust.
And usually they are between 1 and 3. 1 is the slowest flow rate and 3 is the highest. On many properties, we have been to that have had radiators not getting hot, or the whole system not getting to temperature, the pump flow rate is the issue.
Locate the boiler pump. On top of the pump will be a switch. If this switch is set to 1 or 2, there’s a good chance that the flow rate is too low. The pump can be flicked to 3 which is the most powerful setting.
It’s worth consulting a Gas Safe engineer first. The pump may be set at 1 or 2 for a reason (such as a system doesn’t allow any further flow due to microbore pipes). Turning the setting up on a system that doesn’t require it could result in leaks or broken components in the boiler.
Boilers leak for a whole host of different reasons. One of the most common reasons that a boiler leaks is issues with the pump. This can be down to incorrect installation, the pump working itself loose, or even a blown seal due to incorrect pressure settings.
Check that the pump is secure. If it’s not, tightening it up can sometimes be enough to stop a leak.
Check all the fittings on the pump. Corrosion maybe the cause of the leak. If this is the case a new pump will need to be fitted.
Finally, check the joint on the pump. If this is what is leaking, there’s a good chance that it’s the seal on the pump that is blown.
The two options here are to replace the seal, or replace the pump. If the pump is particularly old, a replacement is the best option.
If the pump and boiler have no power, but your property has power, the likely cause is going to be the PCB unit. Hopefully, your boiler has power. If it’s just the pump that has no power (or won’t start up) there’s likely a wiring issue. On some occasions, small leaks can ruin the wiring on the pump.
First, start with the easy and obvious. Like other appliances pumps have fuses. Check that the fuse isn’t blown.
Also, check that are no leaks. If there isn’t, have a Gas Safe engineer come and check the wiring to the pump.
If the pump is old and corroded, there’s a good chance that other parts are going to fail and a replacement is likely in order.
Most pump problems are related to pumps not working. However, on rare occasions we are called out to boilers where the pump constantly runs and won’t switch off. We’ve seen this to be a problem with the Baxi Solo range on a number of occasions.
A proper pump diagnostic needs to take place. In the past, we’ve seen pumps constantly running due to:
- Faulty PCBs (the circuit board on the boiler).
- Pump overrun stat is faulty.
- The mid position valve is sticking (this can be lubricated with WD40).
If you have any questions relating to heating pump problems, please leave a comment below and we’ll get back to you. And we have another article covering heating and boiler problems here.
And, if you want a quote for boiler repair, click here.